For circular stranded copper conductors to DIN 48201 and circular stranded/sector-shaped stranded copper conductors to DIN VDE 0295
E-Cu, DIN 40500/2, F-25
|Cat. No.||Conductor Cross|
Section sq. mm.
|Die Code||Dimensions mm.||Weight
100 pcs. Kg's
The compression cable lugs are marked with a code number in front of the logo (roughly corresponding to the outer diameter of the compression sleeve). The required compression die is selected in accordance with this code number.
For hexagonal compressions made with hand-operated mechanical compression tools, browned dies (black) are to be used for copper cable lugs, whereas aluminium cable lugs require electro-galvanized dies (white).
For hydraulic compression tools there is no differentiation of dies for copper or aluminium cable lugs.
The compression sleeve of aluminium cable lugs is pre-filled with compression compound which must not be removed before the compression, neither completely nor in part. Any compression compound escaping during the compression should be wiped off.
Copper cable lugs are not pre-filled with compression compound.
- Clean the conductor or cable ends with a wire brush to remove dirt and oxidation.
- Insert conductor or cable ends into the compression sleeve up to the stop.
- Before proceeding, make sure that the code number on the cable lug matches that on the compression die.
- Cable lugs are compressed by starting from the plate end and working out toward the sleeve end. The number of compressions is marked on the sleeve. It is important to make the specified number of compressions.